UNIFIED POWER FLOW CONTROLLER CONTROL STRATEGIES for POWER FLOW

In order to address power flow control issues, this study introduces the use of Unified Power Flow Controller (UPFC) models. These models are based on regulating the variables influencing the transmission line’s power flow, and they are capable of controlling the bus voltage, the line’s actual and reactive power, all at once and independently. The idea behind the UPFC technique proposed in this paper is to provide the unique functional capability of independently controlling both the real and reactive power flow in the line. The in-phase component of the series injected voltage dominates the reactive power while the quadrature component affects the real power. A conventional controlling steady-state analysis and dynamic stability analysis of the power system is developed based on the UPFC model. UPFC provides real-time controlling of all or any combination of the power system parameters which determine the transmittable power. UPFC can force and maintain strategically chosen values of the active power and the reactive power at a given point of the line by PI control.


INTRODUCTION
Large electric power networks with extensive geographic coverage, many generators, loads, and interconnection links are characterized by extremely complicated structures.Both static and dynamic complexity might be considered in this context. 1Adding to the complexity of these systems is the inclusion of some renewable energy sources like wind and photovoltaic. 2,3As a result, the power system needs some flexibility to operate through some controllable devices.Among these devices, Flexible AC transmission systems (FACTS).][10] This categorizing is based on how they link to the power supply.The most effective FACTS device that has combine the feature of the series and shunt compensators is UPFC.
The implementation of UPFC models in power flow is a controlled power flow problem.The UPFC has control over all the parameters affecting power flow on the transmission line.UPFC is capable of controlling the real and reactive power on the transmission line and the bus voltage si-multaneously and independently.It can provide the unique functional capability of independently controlling both the real and reactive power flow in the line, these capabilities make the unified power flow controller the most powerful device presently available for transmission system control. 11,12The UPFC, which was proposed by L.Gyugyi, [13][14][15] is one of the most complex FACTS devices in a power system today.It is primarily used for independent control of real and reactive power in transmission lines for a flexible, reliable, economic operation and loading of the power system.A.M. Sharaf and M.S.Elmorsy 16 presented a dynamic controller for STATCOM to stabilize Wind Energy.D.Arabkhaburi, A.Kazemi, M.Yari, and J.Aghaei 17 presented an optimal placement of UPFC in power systems using Genetic algorithm.Y. Xiao et al 18 used an approach to steadystate power flow control of flexible ac transmission systems (FACTS) device-equipped power systems.
The linearized model of the power network including UPFC is useful for small-signal analysis and damping controller design.The UPFC linearized model can be found in. 19,20J. B. Choo et al. 21presented an electromagnetic transmitted simulation model of UPFC, and applied this model to analyze the effectiveness of its operation in the power system.T. Orfanogianni and R. Bacher 22 described the steady-state flexible ac transmission ac transmission systems (FACTS) models and their integration in an optimal power flow.A. Arsoy et al. 23 discussed the incorporation of superconducting magnetic energy storage (SMES) coil into a voltage source converter based static synchronous compensator in damping dynamic oscillations in power systems.
The UPFC dynamic model knowns as a fundamental frequency model can be found in. 24This model consists of two voltage sources, one connected in shunt, and the other one in series with the power network to represent the shunt and series voltage source converters, both voltage sources are modeled to inject voltage of fundamental power system frequency only.The UPFC basic control design involves control of real and reactive power flow, sending bus voltage magnitude and DC voltage magnitude is proposed by K.E.Schoder. 25J. Yong Liu et al. 26 proposed a power injection model (PIM) based UPFC control approach to consider several internal limits imposed on the UPFC, including series injection voltage magnitude, line current through the series converter, real power transfer between the shunt converter and the series converter, shunt control side current and shunt injection voltage magnitude.
H. Cai et al 27 was investigated the power transfer capacity for systems with a unified power flow controller (UPFC).They studied the effects of equipment constraints, system topology and installation locations on the UPFC real power transfer.L. Dong et al. 28 presented the schematic and basic controls of a reconfigurable FACTS system that can be used to realize the major voltage-source converter.
All controllers in references above are PI-type, they are designed for a specific operating condition using a linearized model.However, changes in operating conditions may have a negative effect on the controller performance.PI controllers were presented extensively to control some FACTS devices in modern power systems.STATCOM was presented to regulate the integration of two renewable sources, PV and WECS to the grid through optimal PI controllers. 29Another adaption of STATCOM that was controlled by PI controllers to mitigate the ferorreonanace of WECS was investigated in. 30UPFC was presented for improving the integration of wind energy systems to the grid as in. 31Fractional order PI controller as a modification for the classical PI controller was presented for many FACTS devices as in 32,33 More advanced control schemes such as variable structure control, sliding mode control; offer better dynamic performance than conventional controllers.A variable structure control for a unified power flow control is proposed in this paper.Variable structure system control (VSSC) is attractive because it covers a wide range of operating conditions and is simple to implement.
In this paper, four representative cases have been selected, the first three cases show the UPFC independently controlling the line active power "P", the reactive power "Q", the line impedance "x".The fourth case is for the UPFC to maintain a constant voltage.In all cases, the UPFC is operating with the shunt inverter (STATCOM), and the series inverter (SSSC).The power transmitted over an ac transmission line is a function of the line impedance, the magnitude of the sending-end and the receiving-end voltages, and the phase angle between these voltages.The unified power flow controller (UPFC) was devised for the real-time control and dynamic compensation of the transmission systems, providing multi-functional flexibility required to solve many of the problems facing the demand power as shown in Fig. 1.
[42][43][44][45][46][47][48][49] The operation of each control is mainly dependent on the UPFC mode of operation.In this investigation, the series inverter is controlled to operate in automatic power flow mode, and the shunt inverter is operated in an automatic voltage control mode.In reactive power flow control mode, the shunt converter translates the reactive power reference into a required shunt current and adjusts the signal gate of the converter to establish the desired current.The control uses current feedback signals obtained from the output shunt current to enforce the current reference, the feedback signal representing the dc bus voltage is used to ensure the dc-link voltage.In voltage control mode, the shunt converter reactive current is automatically regulated to maintain the transmission line voltage to a reference value.The automatic voltage control uses voltage feedback signals, representing the magnitude of the bus voltage.

SHUNT AND SERIES CONVERTER MODES
The inverter is operated to absorb or generate the reactive power from the ac system, in addition, it provides the real power demand of the series inverter.The shunt inverter modes of the operation are dependent on the required value used to derive the magnitude and the phase angle of the inverter output voltage as shown in Fig. 2.
It is considered as a terminal voltage regulation as the transformer tap-changer which having infinitely steps.Where the injected shunt voltage in-phase or anti-phase with the bus voltage. 14,20,24,25Where is the sending-end Voltage V sd is the sending end voltage in d-axis V sq is the sending end voltage in q-axis is the current injection is the receiving-end Voltage δ = δ s -δ r is the difference angle X sh is the shunt reactance is the shunt current injection is the STATCOM Voltage V rd is the receiving end voltage in d-axis V rq is the receiving end voltage in q-axis At the sending-end bus, the power is given by Then, the active and reactive power at the sending-bus "s" is given by: So, the power injected by the shunt converter is given by: Finally, the active and reactive power injected by the shunt converter is given by: However, the terminal voltage is given by: The in-phase and the quadrature shunt voltages are: If the reactive current is zero " I sh-q = 0" Therefore, the quadrature shunt voltage provide an adequate reactive power to maintain the terminal magnitude bus voltage at the desired value.For the Shunt voltage control mode, the converter output voltage (V sh ) may be split into two components (V sh-d and V sh-q ) with respect to the a.c.system bus voltage at which the UPFC is connected.The in-phase bus voltage component may be used to control the system bus voltage.The quadrature voltage component allows the shunt in- verter to exchange the real power with the a.c.system which is required for the series inverter.
In the Reactive power mode, the converter output voltage may be divided into two perpendicular components.The in-phase voltage component will allow the shunt inverter to exchange the real power with the d.c.link and the quadrature voltage component is responsible for the exchange of the reactive power with the a.c.system, this in turn supports the reactive power in the transmission system irrespective of the variation of the bus voltage.
In series converter the operation is divided into different modes, these modes dependent on the required value used to derive the magnitude and the phase angle of the injected voltage.The reference signals are the line current and the system bus voltage as shown in Fig. 3.
Where is the SSSC Voltage X se is the series reactance is the series current injection V sed is the series end voltage in d-axis V seq is the series end voltage in q-axis The injected power by the series converter is given by: The active and reactive power injected by the series converter is given by: To control the power flow towards the receiving the receiving-end bus, we have: The active and reactive power injected (V r-q = 0) by the series converter is given by: where, the desired currents are calculated by: The injected voltage V se is adjusted to be in-phase or antiphase with the bus voltage.The injected voltage can be split into two components which are in-phase component " the real power", and in quadrature component "reactive voltage" with the transmission line current.The injected voltage with regular relationship with respect to the receiv-  In series impedance mode, the injected voltage is maintained to be in phase with the line current.The injected voltage compensates for the reactive components of the transmission system impedance when it is perpendicular to the line current and its magnitude is proportional to the current magnitude.
By controlling the magnitude and phase angle of the line current, the active and reactive power of the sending and the receiving ends can be controlled.The shunt inverter must supply the active power of the series converter.

UPFC CONTROL STRATEGY (TECHNIQUE)
The UPFC control system has two main parts, the series converter controller and the shunt converter controller.The operation of each control is mainly dependent on the UPFC mode of operation.

SHUNT CONVERTER CONTROL
The shunt converter may provide reactive power to control the voltage magnitude at the UPFC's sending end bus.If a constant dc terminal voltage is required, the shunt converter, also, needs to generate or absorb real power to the dc terminal as determined by the series converter.In contrast to the series converter, the shunt converter operates under a closed-loop current control structure whereby the shunt real and reactive power components are controlled independently.Therefore, the control strategy of the shunt converter will be different from that of the series converter.The block diagram for the shunt converter is shown in Fig. 4 An instantaneous 3-phase set of the transmission line voltage V s , at bus "s" is used to calculate the shunt magnitude and phase angle of .The STATCOM current I sh is decomposed into its real or direct component I sh-d , and the reactive or quadrature component I sh-q , respectively.An instantaneous 3-phase set of measured V s at bus "s" is decomposed into its direct component V s-d , and quadrature component V s-q , respectively.As seen in Fig. 4, the d-axis current will be regulated by the dc voltage, and the q-axis current will be regulated by the d-axis voltage.If the dc capacitor voltage is allowed to vary according to the prevailing shunt compensation.
demand to reduce the converter losses and harmonics, then the shunt converter will control the angle φ sh directly instead of V sh-d .So that the shunt converter may keep a constant maximum voltage modulation ratio between the converter output voltage and the dc capacitor voltage.In this case, the shunt converter of UPFC will operate as a static Var compensation.In this section, a state feedback linearization control for the STATCOM to control the real power flow through the line, while regulating the voltage magnitude connected with the STATCOM is proposed.
The control inputs v shd and v shq will be Where u shd and u shq are the feedback regulating voltages.
To get the second order response described by the following transfer function where a is the system coefficient, and k p and k i are the PIcontroller gains.By comparing with the second-order system with damping ratio ξ and undamped natural frequency , we get;

SERIES CONVERTER CONTROL
The control for the VSC2 (SSSC) works in such a way that the desired real and reactive power P r are passed through the controllable, which produces, with respect to the bus voltage.The direct and the quadrature components of the series injection voltage V se-d and V se-q , respectively, so, the magnitude of the series voltage and its phase angle and by adding a relative angle α se are calculated.
With proper converter control, this series connected voltage source V se can vary rapidly and continuously to meet the requirement of fast tracking of the power reference, the series converter responds directly and independently to the demand for series voltage injection and changes in series voltage can be effected instantaneously.The control of the UPFC series converter is based upon the vector control approach, it can be seen that control of the power and the reactive power can be obtained by controlling the real and reactive components of the line current (I se-d , I se-q ) , separately.By choosing the controller gain, the current i se-d and i se-q will be able to track the reference currents i se-d ref and i se-q ref in the desired way.The control block diagram is depicted in Fig. 5 As shown from above figure a state feedback linearization control for the SSSC to control the real power flow through the line is proposed.
The control inputs v sed and v seq will be Where u sed and u seq are the feedback regulating voltages.
Similar to the shunt compensation control, we get;

UPFC CONVERTER CONTROL
A combination of a static shunt synchronous compensator -STATCOM, and static synchronous series compensator-SSSC, which are coupled via a common DC link, allows bidirectional flow of the real power between the series output terminals of the SSSC, and the shunt output terminals of the STATCOM, it is used to provide the real and the reactive series line compensation without an external energy source .
The following power flow control functions can be accomplished : The UPFC has several operating modes.Two control modes are possible for the shunt control  The overall block diagram of the UPFC control and the interface with the power system is shown in Fig. 6 To characterize the behavior of the UPFC for the implementation of the automatic power flow controller using the series-connected SSSC, and the bus voltage control using the shunt-connected STATCOM.
The voltage V dc , across the dc link capacitor is maintained by the instantaneous power balance equation at both AC and dc sides of the two converters as sh own in Fig. 7 The power balance equation is given by: Let Where, the ƒ 1 and ƒ 2 are selected to ensure the set value of the dc voltage.If, we want to control the active power only then; Let assume, V se-d =0 Then If, we want to control the reactive power only then; Let assume, V se-q =0 Then

VARIABLE STRUCTURE CONTROL
In any modeling task, two often-conflicting factors prevail "Simplicity" and "Accuracy".These factors lead to desirable attributes for a system model "reduced computational and simplified structures".These properties are of more concern for systems, with high dimension and composite interactions, referred to generally nonlinear systems. 2,3he nonlinearities and complexities can cause computational and analytical difficulties not only in modeling, control, or optimization, but also in the fundamental issues of stability, controllability, and observability.It is therefore natural to seek techniques that reduce the computational effort.
Generally, control of a nonlinear system is accomplished by linearizing the system's equations and using feedback for example to place the system's eigenvalues in the lefthalf of the complex plane.The disadvantage of this linearization method is that the feedback control is valid only in the neighborhood of the operating point about which the system's equations were linearized [88-96].Approaches and methodologies of nonlinear systems provide such techniques through the manipulation of system structure in • The line impedance emulation mode: the reference input is an impedance value to insert in series with the line impedance.• The Automatic power flow control mode: the reference inputs are the values of the active and reactive powers to maintain on the transmission line despite system changes.
UNIFIED POWER FLOW CONTROLLER CONTROL STRATEGIES for POWER FLOW Yanbu Journal of Engineering and Science some way.Thus there has been considerable interest in the research area of modeling, analysis, optimization and control of nonlinear dynamic systems.

RESULTS AND DISCUSSIONS
4.1.SHUNT CONVERTER CONTROL Fig. 8 shows the change in the transient performance of the STATCOM compensation with PI-controller (k p =R sh /L sh -2ξω n , k i =ω n 2 , ξ=1.2, ω n =3.2/t s ξ, and t s =0.01 sec.) using the approximate model [14,48].In this test, the STATCOM command is to decrease the active power from P 0 to P 0 -ΔP.The objective of the controller is to maintain the bus voltage and the reactive power unaltered.This case starts with the STATCOM slidling near the nominal value P 0 =0.058 p.u., the shunt converter regulated the bus voltage to 1.06 p.u.The STATCOM was commanded to decrease the real power to 0.024 p.u..It did this by injecting a voltage about 0.05 p.u. roughly in quadrature with the bus voltage.Throughout this test, the bus voltage was tightly regulated at 1.05 p.u. and the reactive power on the line maintained constant.In Fig. 8 shows the change in the transient performance of the STATCOM compensation with PI-controller using the approximate model.In this test, the reactive power is decreased from Q 0 to Q 0 -ΔQ 0 , while the objective of the controller is to regulate the bus voltage and keep the active power constant.
as shown in the figure 9 above, the STATCOM was commanded to decrease the reactive power to -0.004 p.u.Throughout this test, the bus voltage was tightly regulated at 1.05 p.u. and the active power on the line maintained constant.Fig. 10 shows the change in the transient performance of the STATCOM compensation with PI-controller using the approximate model.In this test, the active and reactive power from P 0 to P 0 -ΔP 0 , and Q 0 to Q 0 -ΔQ 0 , while the objective of the controller is to regulate the bus voltage.
Figure 10 below illustrate the STATCOM was commanded to decrease the active and reactive power.Throughout this test, the bus voltage was tightly regulated at 1.05 p.u. and the active power on the line maintained constant.

SERIES CONVERTER CONTROL
Figure 11 illustrate the change in the transient performance of the SSSC compensation with PI-controller using the approximate model.In this test, the active power is decreased from P 0 to P 0 -ΔP, while the objective of the controller is to maintain the bus voltage and the reactive power unaltered.
Figure 12 shows the change in the transient performance of the SSSC compensation with PI-controller using the approximate model.In this test, the reactive power from Q 0 to Q 0 -ΔQ 0 , while the objective of the controller is to regulate the bus voltage and keep the active power, constant.
Figure 13 shows the change in the transient performance of the SSSC compensation with PI-controller using the approximate model.In this test, the active and reactive power are decreased from P 0 to P 0 -ΔP 0 , and Q 0 to Q 0 -ΔQ 0 , while the objective of this test is to regulate the bus voltage.
Figure 14 shows the change in the transient performance of the SSSC compensation with PI-controller using the approximate model.In this test, the bus voltage is decreased from V to V-ΔV.The objective of the controller is to produce a voltage change.
It is very interesting to note that the changes in the active and reactive powers "P,Q" at the line terminals are balanced by equal and opposite changes in the reactive output of the shunt converter, which acts to maintain the bus voltage.The UPFC reference for the active and reactive powers are changed from P to P-ΔP and from Q to Q-ΔQ, the UPFC forces the change by injecting about Δv se in anti-pahse with v s , the line voltage v r is consequently reduced in magnitude, or in-phase with v s , so that, the line voltage v r is increased.

CONCLUSION
This research analyzes the effects of the UPFC control factors on the transmitted power system.The in-phase component of the series injected voltage dominates the reactive power while the quadrature component affects the real power.In this paper, the STATCOM and the SSSC control strategies are analyzed, and the UPFC model which is suitable for both steady-state analysis and dynamic stability analysis of power system is developed.From the viewpoint of conventional control.The unified power flow controller can provide real-time control of all or any combination of the power system parameters which determine the transmittable power.Thus, the UPFC can fulfill all the functions of reactive shunt compensation, series compensation thereby meeting multiple power flow control objectives.However, the UPFC can also be viewed as a generalized power flow controller that is able to maintain prescribed and independently controllable real power and reactive power in the line.The capability of the UPFC to force and maintain strategically chosen values of the active power and the reactive power at a given point of the line by PIcontrol.

Figure 1 .
Figure 1.Single Line Diagram of Power Transmission System with UPFC

Figure 2 .
Figure 2. Single Line Diagram of Power Transmission System with STATCOM

Figure 3 .
Figure 3. Single Line Diagram of Power Transmission System with SSSC UNIFIED POWER FLOW CONTROLLER CONTROL STRATEGIES for POWER FLOWYanbu Journal of Engineering and Science

Figure 4 .
Figure 4. Block Diagram for Shunt Converter Control

Figure 5 .
Figure 5. Block Diagram for Series Converter Control The UPFC can be operated by the control of the series voltage, in the following different ways: • The terminal voltage regulation • The series line compensation with the terminal voltage control • The phase angle regulation with the terminal voltage control • The terminal voltage regulation with the series line compensation and the phase angle regulation • VAR control mode: the reference input is an inductive or capacitive var request • Automatic Voltage control (AVC) mode: the aim is to maintain the transmission line voltage at the connection point to a reference value • Direct voltage injection mode: the reference inputs are directly the magnitude and the phase angle of the series voltage • The phase angle shifter emulation mode: the reference input is phase displacement between the sending-end voltage and the receiving-end voltage

Submitted: October 22
, 2022 AST, Accepted: December 05, 2022 AST UNIFIED POWER FLOW CONTROLLER CONTROL STRATEGIES for POWER FLOW

Figure 8 .
Figure 8.The transient performance of the STATCOM in case of active power variation with PI-controller

Figure 9 .
Figure 9.The transient performance of the STATCOM in case of reactive power variation with PI-controller

Figure 10 .
Figure 10.The transient performance of the STATCOM in case of Active and Reactive Power Variations with PI-controller

Figure 11 .
Figure 11.The transient performance of the SSSC in case of active power variation with PI-controller

Figure 12 .
Figure 12.The transient performance of the SSSC in case of reactive power variation with PI-controller

Figure 14 .
Figure 14.The transient performance of the SSSC in case of Voltage Variation with PI-controller This is an open-access article distributed under the terms of the Creative Commons Attribution 4.0 International License (CCBY-4.0).View this license's legal deed at http://creativecommons.org/licenses/by/4.0 and legal code at http://creativecommons.org/licenses/by/4.0/legalcodefor more information.